Control and Monitoring—Extend contact I/O for SEL information processors. Monitor the status of external contacts transmitted via SEL Fast Meter messages to a communications processor, and control contact outputs using SEL Fast Operate commands.
Improved Safety—Circumvent dangerous ground potential rise, and increase safety with less dc ground exposure. The SEL-2516 Remote I/O Module also adds self-testing and automatic communications path checking.
Status Annunciation—View the state of each of the eight digital inputs and eight digital outputs with LED indication.
Reliable in Harsh Environments—Place near primary substation equipment to eliminate long runs of copper wiring in the substation yard. Fiber-optic cables not only save money on copper wiring, but also improve data reliability.
Additional Monitoring and Control
Eight digital inputs monitor the status of external contacts that are transmitted via SEL Fast Meter messages to a communications processor. Control eight contact outputs using SEL Fast Operate commands.
Replace control wiring to outside cabinets with fiber-optic cable to eliminate paths for dangerous voltages. All I/O terminals are behind the panel.
Allow clear indication of system function and status.
Easy Installation and Service
Install the rack-mount, compact two rack-unit chassis. The SEL-2516Screw-Terminal Connectorized (STC) blocks for easy replacement of the unit. DIP switches are used to set basic operating parameters.
Fiber-optic links reduce or eliminate data errors from electromagnetic interference. The SEL communications processor monitors the fiber-optic connection to the SEL-2516. The communications processor creates alarms when the fiber-optic cabling is damaged, disturbed, or disconnected.
|Transceiver Compatibility||Connectors||Fiber||Distance(km)||SEL Fiber-Optic Cable|
|SEL-2800||V-System||Multi-mode||0 to 1/2||SEL-C805|
|SEL-2815||ST||Multi-mode||2 to 15*||SEL-C807, C808|
|SEL-2830||ST||Single-Mode||16 to 80*||SEL-C809|
|SEL-2812||ST||Multi-mode||0 to 4||SEL-C807, C808|
*For distances below the minimum, use attenuators on the Transmit fiber.