Current Reset Fault Indicators can be installed on underground systems. CRs are powered by the load current present on an energized line. A CR indicator will respond to a fault and remain in the faulted-display condition until the line is energized with normal line load; at which time, it will automatically reset.
UV-stabilized housings, stainless steel, and vinyl-coated clamping mechanisms make CR Fault Indicators suitable for use in the harsh environments of underground applications.
Years of Maintenance-Free Operation—Apply this energy-harvesting fault indicator in pad-mounted and underground distribution equipment without elbow test points.
Ideal Fault-Finding Solution—Apply to primary 200 A class and 600 A class URD feeders in any medium-voltage radial distribution circuit. Install on medium-voltage primary underground cable applications or on low-voltage secondary lines in industrial environments. The unit automatically resets upon restoration of load current.
Time Savings and Safety—Use remote display options, such as the RadioRANGER Wireless Fault Indication System, to eliminate the need to open a pad-mounted or subsurface enclosure to determine fault status.
Report Back to SCADA—Choose the auxiliary contact option for SCADA compatibility.
|Current Reset||Load current ≥3 A|
|Current Reset||50 to 1,200 A|
|Fault Powered||200 to 800 A|
|Maximum Fault||Current 25 kA for 10 cycles at 60 Hz|
|Trip Response Time|
|Current Reset||1 ms at trip rating (24 ms optional)|
|Outer Diameter Clamping Range||0.75" to 2.10" (please specify clamping diameter or range when ordering)|
|Reset Requirements||3 A|
|Housing Material||UV-stabilized polycarbonate resin|
|Clamp Material||Vinyl-coated silicon steel|
|Submersibility||Up to 15 feet|
|Temperature Range||—40° to +85°C|
|Standard remote “V”|
|Large remote “L”|
|Magnetic probe (RadioRANGER Wireless Fault Indication System required)|
|DT||Delayed trip (24 ms)|
|L||Large core 1.8" to 2.5"|
|W||Window-mounting kit for large remote display|
|?||Show / hide this help menu|