Simple Device Integration—Design and configure SEL devices in IEC 61850 installations using acSELerator QuickSet SEL-5030 Software and Architect together. Architect provides a means to configure and document the IEC 61850 communications settings between SEL devices and devices from multiple manufacturers.
Import and export Edition 1 and Edition 2 Substation Configuration Language (SCL) files to simplify system implementation.
Detect and report errors by automatically comparing SCL files with the IEC 61850 requirements.
SCL files include:
SCD—Substation Configuration Description.
ICD—IED Capability Description.
CID—Configured IED Description.
Easily apply the software with these tools:
IED palette manager.
Create and edit custom buffered and unbuffered MMS reports.
Configure the publications and subscriptions for IEC 61850-9-2LE Sampled Values.
Create and organize custom logical devices.
Server Model Editor—The SEL Real-Time Automation Controller (RTAC) includes MMS server capability that expands the RTAC’s very flexible data concentration capabilities. In systems where the RTAC needs to transmit SCADA data from various client protocol connections (such as SEL, Modbus, or DNP3) in MMS messages, Architect includes the Server Model Editor for configuring MMS server instances in RTACs.
The Server Model Editor provides a graphical representation of the RTAC server model, which enables quick visualization and convenient editing tools for creating and maintaining MMS server applications.